Payment & Shipping Terms:
|Material:||Carbon Steel/ Stainless Steel||Working Pressure:||2-8 Bar|
|Tank Size:||24-48 Inch||Flow Rate:||6-2000 M3/H|
|Control Method:||DP/Time/manual/PLC||Voltage:||220V/50hz(can Be Customized)|
|Keyword:||Automatic Sand Filter||Pressure:||0.15-1.0Mpa|
auto backwash sand filter,
sand separator filter
Industrial process water filtration (nozzle, heat exchange station water protection filtration), industrial circulating water filtration (steel, metallurgy, paper, heat exchanger, electricity, petrochemical, food, air conditioning systems, etc.), raw water treatment filtration (surface water, river water , river water, lake water, sea water, etc.) Irrigation and filtration (water filtration in farmland, parks, municipal and golf courses; water filtration in industries such as aquaculture, swimming and water parks)
>Min. pressure: 0.15Mpa
Sand filter specification sheet table
|Models||Diameter(mm)||Inlet and outlet(mm)||Back washing flow(m3/h)||Filtering area(m2)||Flow (m3/h)|
The Filtering Process
Filtering with media filters, also known as depth filtration, is done by filtering water through a thick layer of graded particles, called the filter bed. These particles can be sand, gravel or other granular materials. The filtration degree depends on the effective size of the bedding and the water velocity through the filter.
Raw water enters from the filter inlet (1) and percolates through the filter bed (2). Suspended materials come into contact and attach to the media particles. Clean water flows through the filtration nozzles (3) and out of the filter via the outlet valve (4).
The gradual dirt buildup in the filter bed causes an increase in the pressure differential across the filter and when it reaches its maximum design value, a cleaning process should be performed. In automatic media filter installations a pressure differential switch senses the pressure differential and when it reaches a preset value, the self cleaning process begins.
The Cleaning Process
Cleaning is done by backwashing; pressurized water flows in reverse direction – from the nozzles upwards, causing suspension of the filter bed, thus releasing the suspended matter from the bedding. The dirt particles are then washed out of the filter through the back-flush valve. In automatic media filters installations the cleaning process is done by the system's controller. When the pressure differential switch senses that the differential pressure across the system reached a pre-set value, a signal is sent to the flushing controller and the self cleaning process begins.
Multi vesseles sand filter system dimensions
Contact Person: Yang